Used to supply power, usually from a pole-mounted transformer, to the user's service head where connection to the service entrance cable is made. To be used at voltages of 600 volts phase-to-phase or less and at conductor temperatures not to exceed 75°C for polyethylene insulated conductors or 90°C for crosslinked polyethylene (XLP) insulated conductors.
|Stock #||10511404 10511404|
|No. of Conductors||3 3|
|Size (AWG or kcmil) (mm2)||1/0 AWG 1/0 AWG|
|No. of Strands||9 9|
|Insulation Thickness (mils) (mm)||60 1.52||mils mm|
|Nom. OD (mils) (mm)||1019 25.90||mils mm|
|Nominal Total Weight (lbs/1000') (kgs/km)||387 576||lbs/1000' kgs/km|
Southwire's triplex service drop cable meets or exceeds the following ASTM specifications:
Conductors are concentrically stranded, compressed 1350-H19 aluminum. Insulated with either polyethylene or crosslinked polyethylene (XLP). Neutral messengers are concentrically stranded 6201, AAC, or ACSR.