Southwire's Romex ® SIMpull ® NMD90 cables may be used for both exposed work in dry locations or concealed work in dry or damp locations. The maximum allowable conductor temperature is 90°C. The minimum recommended installation temperature is minus 25°C for three-conductor cables (with suitable handling procedures). Material should be properly stored above 0°C for 24 hours prior to installation. The maximum voltage rating for all intended applications is 300 volts. Consult the Canadian Electrical Code for further information related to applications.
|Conductor||Ground Wire||Allowable Ampacities+|
|Size (AWG or kcmil)||No. of Strands||Size (AWG)||No. of Strands||Nom. OD (mils) (mm)||Nominal Total Weight (lbs/1000') (kgs/km)||Allowable Ampacity at 60C||Allowable Ampacity at 75C||Allowable Ampacity at 90C|
|562387||6 AWG 6 AWG||7 7||8 8||7 7||753 19.15||219 326||40 40||50 50||55 55|
|586871||4 AWG 4 AWG||7 7||6 6||7 7||934 23.75||359 534||55 55||65 65||75 75|
Southwire's Romex® SIMpull® NMD90 cables meet or exceed the requirements of:
The 3 conductor colours are black" red and white with PVC jacket.