Southwire PVC Jacketed HCF MCAP® Type MC Cable is suitable for use as follows:
|No. of Conductors||Size (AWG or kcmil)||No. of Strands||Insulation Thickness (mils) (mm)||Size (AWG)||No. of Strands||Nom. OD (mils) (mm)||Nominal Total Weight (lbs/1000') (kgs/km)||Allowable Ampacity|
|584950||2 2||12 AWG 12 AWG||1 1||15 0.38||10 10||548 13.93||156 233|
|599111||3 3||12 AWG 12 AWG||1 1||15 0.38||10 10||628 15.96||193 287|
|644645||4 4||12 AWG 12 AWG||19 19||15 0.38||10 10||637 16.19||225 334|
|597999||2 2||10 AWG 10 AWG||1 1||20 0.51||8 8||647 16.46||185 276|
Southwire PVC Jacketed HCF MCAP® Type MC Cable fully meets or exceeds the following requirements:
Southwire PVC Jacketed HCF MCAP® Type MC Cable is constructed with solid soft-drawn copper Type THHN circuit conductors (rated 90ºC dry), redundant grounding provided by an armor assembly comprised of interlocked armor with a bare aluminum grounding/ bonding conductor, and a green insulated copper grounding conductor. The insulated circuit and grounding conductors are cabled together and wrapped with a binder tape bearing the print legend. The bare aluminum grounding/bonding conductor is located outside the binding tape and has the same lay as the insulated conductors. Green Aluminum interlocked armor is snugly wrapped around the conductor assembly. A black sunlight resistant, flame retardant PVC jacket is applied over the armor. Print legend is included on the binder tape as well as the overall PVC jacket.